FIRE SPRINKLER SYSTEM SERVICES
✓ Annual & Monthly, Quraterly & Weekly Testing, Inspections & Reporting
✓ Wet Sprinker System
✓ Dry Sprinkler System
✓ Deluge System
✓ Pre-Action System
✓ Standpipe Systems
✓ Fire Hydrants
✓ Diesel & Electric Fire Pumps
Sprinkler systems save lives — but only if they are properly maintained. According to NFPA 25, any sprinkler system containing control valves without electronic supervision should be checked on a weekly basis to make sure that they are in the open position. Additionally, at least four times each year, a full sprinkler system inspection should be performed by a certified technician.
DAILY (DURING FREEZING WEATHER)
Check dry pipe valve rooms or enclosure system.
Inspect auxiliary drains to prevent freezing.
Check unsupervised control valves.
Check air and water pressure on dry pipe systems.
Test sprinkler alarms on sprinkler systems that do not have electrical supervisory signal service only.
Inspect valves which are locked open.
EVERY TWO MONTHS
Test supervisory transmitters and water.
Inspect valves that are electrically supervised.
EVERY SIX MONTHS
Test gate valve supervisory switches and other sprinkler and fire protection system supervisory devices.
Check exposed sprinkler system pipe hangers and sprinkler heads.
Inspect dry pipe valve priming level.
Inspect fire department connections, test water flow on wet sprinkler systems.
Trip-test dry pipe trip system (control valve not required to be fully open).
Test flow of water supply – to be completed only by qualified contractor.
EVERY THREE YEARS
Trip-test dry-pipe valves with control valve fully open – to be completed only by a qualified contractor.
EVERY FIVE YEARS
Flushing of the sprinkler system is required
Contact us for a Free Consultation today! email@example.com